* Pepperl+Fuchs makes every effort to provide an answer that is helpful and relevant to you. Your question is typically answered in one business day. Occasionally, an answer is delayed. In these cases, we are often researching your question, conferring with colleagues, or may route your question to another Pepperl+Fuchs location. You will be notified via e-mail regarding the status of your question.
Please note: All product-related documents, such as certificates, declarations of conformity, etc., which were issued prior to the conversion under the name Pepperl+Fuchs GmbH, also apply to Pepperl+Fuchs AG.
Download the complete datasheet as a PDF:
|Operating voltage||6.6 kV|
|Operating current||650 A max.|
|General information||Three equally spaced internal bus bars are mounted on insulators. The insulators are in turn mounted on polycarbonate offering excellent separation between phases. Six plastic cable support cleats are mounted on GRP support rails.|
|Number of busbars||3, each with 2 x M10 thru-holes with terminal lugs suitable for 70mm2 cable|
|Enclosure cover||fully detachable|
|Degree of protection||IP66|
|Cable entry||thru-holes direct through body
or via gland plate
|Gland plate on face(s)||B|
|Enclosure||1.5 mm AISI 316L, (1.4404) stainless steel|
|Gland plate||3 mm AISI 316L, (1.4404) stainless steel|
|Seal||Silicone rubber, one piece|
|Mass||approx. 44 kg|
|External dimension (A)||977 mm|
|External dimension (B)||677 mm|
|External dimension (C)||300 mm|
|Internal dimension (D)||928 mm|
|Internal dimension (E)||628 mm|
|Internal dimension (F)||279 mm|
|Mounting holes distance (G)||902 mm|
|Mounting holes distance (H)||727 mm|
|Mounting holes diameter (J)||11 mm|
|Maximum external dimension (K)||752 mm|
|Grounding||M10 internal/external brass grounding bolt|
|Ambient temperature||-50 ... 55 °C (-58 ... 131 °F)|
|Data for application in connection with hazardous areas|
|EU-type examination certificate||SIRA 00 ATEX 3206|
|Marking||II 2 GD Ex e IIC T6 Gb, Ex tb IIIC T85 °C Db|
|IECEx approval||IECEx SIR 09.0109|
|EAC approval||RU C-DE.BH02.B.00016/18|
|Degree of protection||EN 60529|
|Supplementary information||EC-Type Examination Certificate, Statement of Conformity, Declaration of Conformity, Attestation of Conformity and instructions have to be observed where applicable. For information see www.pepperl-fuchs.com.|
|Instruction manuals||Language||File Type||File Size|
|Installation & Maintenance Manual for HVB6.6 High Voltage Box||ENG||95 KB|
|Installation & Maintenance Manual for HVB6.6 High Voltage Box||RUS||148 KB|
|Certificates||Certificate No.||File Type||File Size|
|Europe Sira II 2GD ATEX||Sira 00 ATEX 3206||173 KB|
|Sira IECEx Certificate of Conformity||IECEx SIR 09.0109||LINK||---|
|Russia Belarus EAC Kazakhstan NANIO "CCVE"||RU C-DE.BH02.B.00016/18||1638 KB|
Get a free PDF copy of our Quick Select Product Guide for Electrical Explosion Protection Equipment. It offers you a comprehensive overview of our entire portfolio.
Use our online tool to quickly configure your individual terminal box.
You receive a tender within a business day!
When ordering within Europe, your custom Ex e terminal box or local control unit is ready for shipment in just five days!